Die-casting aluminum bracket and ABS cover
Actuator can meet different pressure demand
Synchronous motor, equip with shut power function, it can open at any position due to supply stable torque
forward and reversal control setting meet different valve body
1. Reserve enough space for maintenance during installation.
2. The wiring shall comply with the national electrical construction specification, and conducted in the case of power off.
3. The actuator should not be covered by thermal insulation material to prevent it from heat dissipation.
4. Vertical installation should be given priority, and inclined or horizontal installation can be adopted in special occasions, but support and fixation should be added when the volume, weight and vibration are too large.
5. Manual valves are recommended to be installed at both ends of the control valve to facilitate maintenance. During use, grease should be added regularly for three or four months.
6. When the installation position of the control valve is not indicated on the design drawing, the control valve is generally installed on the return water pipe.
1. Insert the actuator into valve stem
2. Tight two screws use hex key
3. Use manual lever to adjust the stroke, then put gasket into slot, last tight the nut
Attention: the assemble must vertical between actuator and valve body
1. Insert handle
2. Rotate "UP" and "DOWN".
Environment Temperature: -5℃~55℃ 2.Storage Temperature：-2℃~85℃ 3. Protect Class: IP 44